“FIX 010 "is made up of press-bent semi-finished pre-galvanized sheet steel. Doors and cover plates are made of painted sheet steel.
The switchboard is composed of an omnibus busbar system situated in the upper part with cable drops on the left side and a cable tray on the right side.
In the case of particularly heavy starts, the power supply can be directly derived from the omnibus busbars.
The subdivision includes a maximum of 10 compartments with double modularity.
The switchboard can be moved with a forklift, being equipped with a sturdy base frame.
The compartments can be fixed to the floor (with screw anchors) or to foundation frames.
|Rated service voltage||690V|
|Rated insulation voltage||1000V|
|Industrial frequency test voltage power circuits||3500V|
|Industrial frequency test voltage auxiliary circuits||2000V|
|Voltage impulse peak for insulation test 1,2/50μs||8000V|
|Main busbar rated current||900-1250A|
|CHalf drop busbar rated current||400-700A|
|Permissible short term current for 1 second for main and drop busbars||50kA|
|Permitted peak current for main and drop busbars||105kA|
|Permissible short term current for 1 second for ground||30kA|
|Permitted peak current for ground||63kA|
|Draw-out units rated current modules 1/14||250A|
|Draw-out units rated current modules 2/14||450A|
|Permissible short term current for 0.2 second for draw-out units||50kA|
|Permitted peak current for drow-out units||105kA|
Compliance with the Law
|Protection degree with open doors||IP20|
|Maxim protection degree with closed doors||IP41|
|Max ambient temperature||40°C|
|Max altitude||2000mt s.l.m.|